Service Entrance, Service Conductors, Service Equipment, Service Grounding.
The Service Entrance Conductors which extend from the point of utility company supply through the wall of a building to the main service.
Electrical Power Service Expert for Hire.
Electrical power design, upgrade, modifications, transformers and repairs for Commercial / Industrial Facilities.
Three Phase, Two Phase, Single Phase, Service Entrance Power Panels and Upgrades.
Our services begin with powerfully good information, a good price, then hard work.
|Switch Gear expert,|
Contact us for assistance and costs.
|Damages, Repairs, Replacements.|
|Changes, Relocation or|
|Parking Lot Trenching.|
Two-Phase Electric Service? Got Limitations? |
Ask me about it.|
Electrical primary and secondary circuits - changes and upgrades. Aerial or underground
utility connections for service entrance power panels. Hard to find circuit breakers, motors and control panels. Two-Phase electrical service experts
for elevator motors and special equipment. High reach bucket truck service. Voltage drop problems, surges, spikes - I have your answer.
Electrical Service Upgrades
200 amp, 400 amp, 800 amp to 2000 amp.
Voltages - 4160V, 13200V, 480V., 277V. 240V., 208V. 120V. Customized panels, power trough and buss duct. Buss Bar modifications and
other fabricated items for any electrical purposes.
Economical Concern for Your Property.
A. to Z. Electrical Power and costs by email,
from Able Group Inc., Havertown, PA
Step up, step down,
The ratio of the peak voltages and peak currents in the primary and secondary windings are
determined by the ratio of the number of turns in the primary and secondary windings. The latter ratio is usually called the turn
ratio of the transformer. If the secondary winding contains less turns than the primary winding, the peak voltage in the
secondary circuit is less than that of the primary circuit.
Let me be your
I know the
old-school electrical ways - Keeping the cost down!
I make repairs to fused disconnects,
magnetic motor starters, electromagnetically operated contacts, push buttons for equipment -
start and stop. I do the research needed for the connected motor load and particular control circuits with momentary contact devices.
Connections to the coil of the magnetic motor starter performs this start and stop function. A 3-pole full-voltage magnetic motor
starter is made up of the following components: a set of stationary contacts, a set of movable contacts, pressure springs, a solenoid
coil, a stationary electromagnet, a set of magnetic shading coils, and the moving armature.
Electrical safety inspections checking your circuit breakers, GFI receptacles, grounding rods
and cold water pipe grounding. We are installers for: main lug panel, cadmium connectors, MC wire, SER cable, SEU cable,
twist-lock receptacles, power poles and floor receptacles for your mid-floor electrical needs.
Service Upgrade Package includes -
Removal of all existing electrical service equipment, cables,
fuse boxes, meter socket, etc. Furnish & Install a NEW Exterior Cable Drop (overhead type service), Meter Socket, Entrance cable,
Circuit Breaker Panel, Circuit Breakers for all circuits and labeled accurately, Code Required Grounding, Final Connections, Clean-up
and as always, ALL TRASH TAKEN AWAY.|
Utility Poles, Installers for Privately Owned Utility Poles - The Able Group.
3Phase - 2Phase Electrical Services in Philadelphia.
Aerial Electrical Cables in Philadelphia.
Apartment Utility Separations in Philadelphia.
CT Cabinets and Electrical Services in Delaware County PA.
Electric Service Upgrade, Philadelphia, PA.
We cover areas surrounding: Delaware County, Chester County, Montgomery County,
Philadelphia, PA. Where multiple sets of service-entrance conductors are used the equivalent size
of the largest service-entrance conductor shall be determined by the largest sum of the areas of the corresponding conductors of each set. 2.
Where there are no service-entrance conductors, the grounding electrode conductor size shall be determined by the equivalent size of the largest service-entrance
conductor required for the load to be served. 3. Where the grounding electrode conductor is connected to made electrodes that portion of the
conductor that is the sole
connection to the grounding electrode shall not be required to be larger than No. 6 copper wire or No. 4 aluminum wire.
4. Where the grounding electrode conductor is
connected to a concrete-encased electrode that portion of the conductor that is the sole connection to the grounding electrode shall not be required
to be larger than
No. 4 copper wire. 5. Where the grounding electrode conductor is connected to a ground ring not smaller than No. 2.
that portion of the conductor that is the sole
connection to the grounding electrode shall not be required to be larger than the conductor used for the ground ring.
Anthony Tori - The electrical contractor. The Able Group Inc.